(A) A building sewer shall have a minimum diameter of four inches.
(B) A building sewer shall be watertight and constructed of durable material, capable of withstanding a ten foot head of water test or equivalent.
(C) Traps shall not be installed in a building sewer.
(D) A building sewer shall be laid in good alignment and embedment at a uniform grade in accordance with engineering practices acceptable to the Ohio department of health.
(E) A building sewer shall be a minimum of ten feet from any household water supply source and water service line.
Promulgated Under: 119.04
Statutory Authority: Sec. 120.02 of Am. Sub. HB 119 (127th G.A.)
Rule Amplifies: Sec. 120.02 of Am. Sub. HB 119 (127th G.A.)
Prior Effective Dates: 7/1/1974, 7/1/77, 7/2/07