Rules 3745-66-90 to 3745-66-101 of the Administrative Code apply to owners or operators of facilities that use tank systems for storing or treating hazardous waste except as otherwise provided in paragraphs (A), (B), and (C) of this rule or in rule 3745-65-01 of the Administrative Code.
(A) Tank systems that are used to store or treat hazardous waste which contains no free liquids and that are situated inside a building with an impermeable floor are exempted from the requirements of rule 3745-66-93 of the Administrative Code. To demonstrate the absence or presence of free liquids in the stored/treated waste, the following test must be used: method 9095B ("Paint Filter Liquids Test") as described in "Test Methods for Evaluating Solid Waste, Physical/Chemical Methods," U.S. EPA publication SW-846.
(B) Tank systems, including sumps, as defined in rule 3745-50-10 of the Administrative Code, that serve as part of a secondary containment system to collect or contain releases of hazardous wastes, are exempted from the requirements in paragraph (A) of rule 3745-66-93 of the Administrative Code.
(C) Tanks, sumps, and other collection devices used in conjunction with drip pads, as defined in rule 3745-50-10 of the Administrative Code and regulated under rules 3745-69-40 to 3745-69-45 of the Administrative Code, must meet the requirements of rules 3745-66-90 to 3745-66-101 of the Administrative Code.
[Comment: For dates of non-regulatory government publications, publications of recognized organizations and associations, federal rules, and federal statutory provisions referenced in this rule, see rule 3745-50-11 of the Administrative Code titled"Incorporated by reference." ]
Cite as Ohio Admin. Code 3745-66-90
R.C. 119.032 review dates: Exempt
Promulgated Under: 119.03
Statutory Authority: 3734.12
Rule Amplifies: 3734.12
Prior Effective Dates: 04/15/1981, 01/07/1983, 12/08/1988, 06/29/1990, 09/02/1997, 12/07/2004