(A) Hazardous wastes or treatment reagents shall not be placed in a tank system if they could cause the tank, its ancillary equipment, or the secondary containment system to rupture, leak, corrode, or otherwise fail.
(B) The owner or operator shall use appropriate controls and practices to prevent spills and overflows from tank or secondary containment systems. These include at a minimum:
(1) Spill prevention controls (e.g., check valves, dry disconnect couplings);
(2) Overfill prevention controls (e.g., level sensing devices, high level alarms, automatic feed cutoff, or bypass to a standby tank); and
(3) Maintenance of sufficient freeboard in uncovered tanks to prevent overtopping by wave or wind action or by precipitation.
(C) The owner or operator shall comply with the requirements of 3745-66-96 of the Administrative Code if a leak or spill occurs in the tank system.
Eff 4-15-81; 1-7-83;
Rule promulgated under: RC Chapter 119.
Rule authorized by: RC 3734.12
Rule amplifies: RC 3734.12
119.032 review date: Exempt
This rule is promulgated so that Ohio may administer a hazardous waste program as required by Section 6926 of the Resource Conservation and Recovery Act ( 42 U.S.C. Section 6901 ET SEQ.) and federal regulations promulgated thereunder (40 C.F.R. Part 271)