(A) Ignitable or reactive waste must not be placed in a tank system, unless:
(1) The waste is treated, rendered, or mixed before or immediately after placement in the tank system so that:
(2) The waste is stored or treated in such a way that it is protected from any material or conditions which may cause the waste to ignite or react; or
(3) The tank system is used solely for emergencies.
(B) The owner or operator of a facility where ignitable or reactive waste is stored or treated in tanks must comply with the requirements for the maintenance of protective distances between the waste management area and any public ways, streets, alleys, or an adjoining property line that can be built upon as required in tables 2.3. 2.1.1(a) and 2.3. 2.1.1(b) and tables 2.3. 2.1.2 to 2.3. 2.1.5 of the national fire protection association's (NFPA) "Flammable and Combustible Liquids Code".
[Comment: For dates of non-regulatory government publications, publications of recognized organizations and associations, federal rules, and federal statutory provisions referenced in this rule, see rule 3745-50-11 of the Administrative Code titled"Incorporated by reference."]
R.C. 119.032 review dates: 04/14/2010 and 08/25/2014
Promulgated Under: 119.03
Statutory Authority: 3734.12
Rule Amplifies: 3734.12
Prior Effective Dates: 04/15/1981, 01/07/1983, 12/08/1988, 12/07/2000, 12/07/2004