(A) The owner or operator of a treatment facility shall inspect, where present:
(1) Discharge control and safety equipment, including, but not limited to, waste feed cutoff systems, bypass systems, drainage systems, and pressure relief systems at least once each operating day, to ensure that such systems are in good working order;
(2) Data gathered from monitoring equipment (e.g., pressure and temperature gauges), at least once each operating day, to ensure that the treatment process or equipment is being operated according to its design;
(3) The construction materials of the treatment process or equipment, at least weekly, to detect corrosion or leaking of fixtures or seams; and
(4) The construction materials of, and the area immediately surrounding, discharge confinement structures (e.g., dikes), at least weekly, to detect erosion or obvious signs of leakage (e.g., wet spots or dead vegetation).
Eff 4-15-81; 1-7-83
Rule promulgated under: RC Chapter 119.
Rule amplifies: RC 3734.12